Job Timeline (Ref 5833-6828)
A Timeline of this job can be seen below.
Satelite Elec. (Zhongsan) Ltd ID8 Remote Repair Details
Manufacturer : Satelite Elec. (Zhongsan) Ltd
Model : ID8
Customers Fault Description : Low works then Off works
Med works Off does not work
Hi works Off does not work
Hi to Med to Low does not work
Low to Med to Hi does not work
Off does not work
Remote Fixer Repair Response (see below) :
This Fan controller arrived safely and on testing was found to have erratic functionality.
On opening the main problem was found to be due to liquid contamination over the button array, this was cleaned up which restored functionality.
On of the battery terminals was also replaced as it was very badly corroded.
Air Conditioning Controller Testing Video
Remote Control Repair Testing Video
Clone was sent ugt 15th 6 2020